Load balancing with the Easee Lite means you will be able to balance the electrical use between up to three Charge Lite chargers and the building.
For load balancing Charge Lite chargers, you must have the following:
- An RCD type A connected to each backplate that is part of the Easee Lite installation.
- The chargers are set up on the same circuit in the Installer app.
- An Equalizer is connected with the chargers on the site.
You can not have more than three Charge Lite chargers per site.
Installing multiple chargers on one site
Setting up an enclosure closer to the chargers will save on cabling.
The RCDs can be installed in the fuse cabinet if there is room.
In each method of installation, there is an RCD A between each Charge Lite and the fusebox. These cannot be wired in a "daisy chain", where you wire pass-through to the next RCD A and Easee Lite. It must be a direct connection from the fusebox to the RCD A, and a direct connection from the RCD A to the Easee Lite.
Load balancing Charge Lites
Once the Charge Lites are properly installed, install the Equalizer and connect each Charge Lite to it.